The function of a Strainer is to remove debris from a refrigerant or
oil line in order to protect the Compressor and other components
Henry Technologies' offers Y-Type Strainers in NPT and ODS connections for
use on air conditioning and refrigeration systems. The Strainers can be used
in refrigerant and oil lines to remove large debris. If greater protection is
desired, Henry Technologies also offers Filters and Filter-Driers.
Henry Technologies' Strainers are suitable for use with HFC and HCFC
refrigerants and their associated oils, as well as other industrial fluids non-
corrosive to brass, steel and synthetic rubber.
Particle retention down to 150 microns
Replaceable 100 Mesh stainless steel screen
Materials of Construction
The Strainer bodies are made of forged brass and the 100 Mesh strainer
cartridge is made of stainless steel. The Strainer Plug is made of brass and
uses a synthetic rubber seal.
Maximum working pressure = 500 PSI (34.4 Bar)
Allowable operating temperature= -20°F to +200°F (-29°C to +93°C)
Henry Technologies' Y-Type Strainers are UL Listed by Underwriters
Laboratories, Inc. Additionally, Y-Type Strainers are designed and registered
for use in Canada. Please contact Technical Support at 1-800-627-5148 for
CRN details and list of approved provinces and territories.
Screen Area (in )
Installation - Notes
1. The Strainers must be installed in accordance with the flow direction
2. ODS series Strainers must be taken apart for brazing.
3. Screen Cartridges should be replaced after a 15 PSI (1 Bar) pressure
drop has been detected.
4. Full instructions are given in the Product Instruction Sheet, included
with each Strainer.